Three phase transformer is mainly used for high power transmission.

To meet the demand for three phase power transmission, transformer connections compatible with three-phase operations are needed.

We can achieve the transformer connections in two ways: by connecting three single-phase transformers, thereby forming a so-called *transformer bank*, or by using a special three-phase transformer.

After we learn about the linear transformer, we will have some important explanation such as:

- Mutual inductance and dot convention
- What is ideal transformer
- Three phase transformer
- Transformer as isolation device
- Transformer as matching device

**Contents**show

For the same kVA rating, a three-phase transformer is always smaller and cheaper than three single-phase transformers. When single-phase transformers are used, one must ensure that they have the same turns ratio *n *to achieve a balanced three-phase system.

## Three Phase Transformer

There are four standard ways of connecting three single-phase transformers or a three-phase transformer for three-phase operations: Y-Y, Δ-Δ, Y-*Δ*, and *Δ*-Y.

For any of the four connections, the total apparent power *S**T*, real power *P**T*, and reactive power *Q**T *are obtained as

where *V*_{L }and *I*_{L }are, respectively, equal to the line voltage *V*_{Lp }and the line current *I*_{Lp }for the primary side, or the line voltage *V*_{Ls }and the line current *I*_{Ls }for the secondary side.

Notice from Equation.(1) that for each of the four connections, *V*_{Ls}*I*_{Ls }= *V*_{Lp}*I*_{Lp}, since power must be conserved in an ideal transformer.

For the Y-Y connection in Figure.(1), the line voltage *V*_{Lp }at the primary side, the line voltage *V*_{Ls }on the secondary side, the line current *I*_{Lp }on the primary side, and the line current *I*_{Ls }on the secondary side is related to the transformer per phase turns ratio *n* as

For the Δ-Δ* *connection in Figure.(2), Equation.(2) also applies for the line voltages and line currents.

This connection is unique in the sense that if one of the transformers is removed for repair or maintenance, the other two form an *open delta*, which can provide three-phase voltages at a reduced level of the original three-phase transformer. This three-phase transformer is used for transformer power distribution system.

For the Y-Δ* *connection in Figure.(3), there is a factor of √3 arising from the line-phase values in addition to the transformer per phase turns ratio *n*. Thus,

Similarly, for the Δ-Y connection in Figure.(4),

Thus,

Read also : equation for capacitor charging circuit

## Three Phase Transformer Equivalent Circuit Example

The 42-kVA balanced load depicted in Figure.(5) is supplied by a three phase transformer. (a) Determine the type of transformer connections. (b) Find the line voltage and current on the primary side. (c) Determine the kVA rating of each transformer used in the transformer bank. Assume that the transformers are ideal.

**Solution:**

(a) A careful observation of Figure.(5) shows that the primary side is Y-connected, while the secondary side is Δ-connected. Thus, the three phase transformer is Y-Δ, similar to the one shown in Figure.(2).

(b) Given a load with total apparent power *S*_{T }= 42 kVA, the turns ratio *n *= 5, and the secondary line voltage *V*_{Ls }= 240 V, we can find the secondary line current using Equation.(1a), by

From Equation.(3)

(c) Because the load is balanced, each transformer equally shares the total load and since there are no losses (assuming ideal transformers), the kVA rating of each transformer is *S *= *S*_{T}*/*3 = 14 kVA.

Alternatively, the transformer rating can be determined by the product of the phase current and phase voltage of the primary or secondary side.

For the primary side, for example, we have a delta connection, so that the phase voltage is the same as the line voltage of 240 V, while the phase current is *I*_{Lp}*/*√3 = 58*.*34 A. Hence, *S *= 240 × 58*.*34 = 14 kVA.

Im a huge fan already, man. Youve done a brilliant job making sure that people understand where youre approaching from. And let me tell you, I get it. huge stuff and I cant wait to read more of your blogs. What youve got to say is important and needs to be read.

faves, since I was here were a few. Well another article that will work out just fine. I need this article just finishing up, fortunately for me it is on a similar subject as this post. Glad, have a good one.